Lihir Island, Papua New Guinea – 2003
First Geothermal Power Station in PNG: Press Release, April 16, 2003
Lihir Gold Limited
“Gold company Lihir Gold Limited is turning its vast geothermal resource into an opportunity. In April, the company started commissioning a 6MW geothermal power station, the first in Papua New Guinea to use natural geothermal energy for the generation of electricity.
Located on Lihir Island in New Ireland Province, all of Lihir Gold’s gold reserve is, to some degree, in geothermal zones. The company has successfully managed Lihir’s geothermal resource so that mining is feasible in areas once considered too hot and, now, following extensive studies, it is using geothermal steam for power generation.
Four steam wells, initially drilled for the purpose of cooling and de-pressuring the mine, will provide the steam required for the power station. The Lihir power plant requires over 100 tonnes of steam per hour to operate at maximum capacity. The 6MW produced represents about 10% of the gold operation’s total power requirements.
Based on last year’s spending on heavy fuel, we expect to save over US$2-million a year following the commissioning of the geothermal power station.”
6MW Non-Condensing Power Plant
Lihir Island, Papua New Guinea – 2003
GDA scope of work comprised plant design, plant component subcontracting, expediting, inspections and testing, assembly, overland shipment to US ports, insurance, performance guarantee and warranty.
The GDA plant supply scope of supply included steam turbine and turbine accessories, including steam turbine, steam inlet piping assembly, hydraulic oil system, control and instrumentation, turbine skid; generator and generator accessories, including generator, exciter, main terminal box and generator skid; speed reduction gear; lube oil console; switchgear and controls, including switchgear, control panel, motor control center, battery and battery charger, and motors; control building, including control building electrical wiring responsibilities; shop assembly and preparation for shipment; design and supervision; and inspections and testing.
The GDA supervision contract on Lihir Island included supervision of unpacking and examination of plant components; supervision of general assembly and complete installation of plant on site; supervise plant testing and startup; training site personnel and overseeing plant commissioning.
A compact lube oil console was designed solely by GDA. It provides lubricating oil for the turbine generator set during both normal operation and in an emergency shutdown situation. The console features AC & DC motors, a centrifuge, a 300 US gallon reservoir and manual/automatic control system components.
In the picture at left, the lube oil console appears to the right, alongside the turbine generator set.
GDA assembled and wired a remote control panel (shown in pictures below). The primary features of the panel are a Quantum PLC, a Woodward electronic governor, a Multilin generator protective relay and an excitation control system. In addition to the turbine generator set, the PLC controls and/or monitors the gearbox, lube & hydraulic oils, cooling water and steam valves/lines. Manual control of some systems is allowed at junction boxes mounted on or near the equipment.
The picture on the left below shows a close-up of the electronic governor, which allows automatic or manual control of plant synchronization to the local utility lines. The screen shows the turbine-generator operating at its design performance of 6000kW.
The Lihir steam turbine began as an unused, low pressure CL-55, originally manufactured for military marine duty. It was modified for geothermal power generation by GE Energy.
In the picture below (right), there is an insulation blanket over the top of the turbine. The silver wrapped piping transports the inlet steam from the geothermal wellfield. On the left side of the picture, the speed reducing gear that connects the synchronous generator and turbine is barely visible. A gauge board for monitoring turbine pressure and temperature is shown on the right.