Leak team gets total success from FIDO-led work orders - Case Study
Thames Water trials FIDO analysis as part of leakage drive and achieves over 92% accuracy.
With 10 million water customers across London and the Thames Valley, Thames Water has a massive water supply infrastructure to manage.
A target of reducing reportable leakage by 20% between 2020 and 2025, meant leakage detection and repair is a major focus for the company.
Thames approached FIDO Tech to help target leakage in a defined region due to increasing challenges around the identification, verification and successful repair of leaks.
The company also wanted to evaluate whether to retain, maintain and expand its existing logger estate of 27,000 devices that is nearing renewal.
The FIDO AI Solution
A four-week trial was set up with Thames’ Leakage Strategy Team to demonstrate the value of the FIDO service. The objective was to show how FIDO AI and FIDO hardware can deliver accurate, objective results with a clear call to action and take leakage teams to within 1m of leaks.
The first step was to run the past four months’ worth of acoustic logger records through the FIDO AI algorithm and classify each point of interest (POI) as either a leak, possible leak or non-leak.
The results identified two DMAs that were of particular concern. Over a two-week period, FIDO leakage engineers accompanied two of Thames’ leakage detection service providers, Hydrosave and RPS, to visit as many POIs in the two DMAs as possible.
FIDO AI analysed over 35,000 historic sound files in 2.5 hours and returned a report which Thames Water retrospectively followed up with its own leakage repair records and dig data.
We then carried out analysis of Thames Water’s entire logger estate, an additional 6,810 new acoustic files. From these daily reports, Thames Water identified 33 POIs for on-site follow verification by its leakage detection service providers and FIDO operational staff.
Of these, 11 led to the discovery of misaligned loggers, and 20 were correctly confirmed as leaks or not leaks (including 4 customer side leaks), an accuracy of over 92%.
Post-trial analysis showed 13 successful digs out of 13 work orders raised. FIDO AI also identified additional POIs which would not have been flagged for investigation using Thames’ traditional detection methods.
All new logger alarm files were processed by FIDO AI overnight to provide a start-of-day report showing new leaks over the full trial period. This allowed Thames Water to create their own logic table of POIs and therefore target, plan and schedule POI visits with greater accuracy.
FIDO also helped demonstrate that the company’s current acoustic loggers were an important and integral part of their leakage process that would support their future leakage strategy.