The manufacturing site is a steam cracker in Europe operating 24 hours 7 days a week. To ensure its production, the plant has three boilers supplying in vapor several steam turbines and furnaces. The monitored equipment is a fan linked to a boiler. Fan is equipped with a magnetic-clutch allowing a driving from either an electrical motor either a turbine.The shafting is historically unreliable, especially at the clutch location. Clutch is mounted on four bearings.
Customer request for Wi-care
Complete bearing and shaft damage occur with very high and fast temperature increase. No system in place was able to detect and react quickly enough. Vibration and temperature monitoring via Wi-care is installed as an ideal solution for fan protection and prediction.
Analyst diagnosis and spectrum justification: Good condition
We detect a peak at 1X RPM (16.9 Hz) on each clutch bearings which indicate an unbalance. The amplitudes are stable and acceptable.
We also detect a peak at 37.5 Hz and at 105.0 Hz matching to the middle and high speed frequency from the coupling gearbox. The levels associated to these frequencies are negligible.
We don’t observe other frequencies which indicate significant fault