1) TheSlurry pump suction piping system does not allow leakage phenomenon, into the pool pump can pump through the grille Multi-stage pumps should be consistent with requirements of the particles in order to avoid large particles of materials or long-fibrous material into the pump causing blockage.
2) To the timely replacement of damaged slurry pump parts easy to cast, maintenance, assembly should be correct gap adjustment is reasonable, may not he to bear in friction phenomena.
3) The bearing pressure, amount of water to meet the requirements at any time to adjust (or replacement) Fill tight Slurry pumps or too loose, do not result in slurry seal leakage. And the timely replacement of sleeve.
4) The replacement of bearings, we must ensure that bearing assembly within the dust, lubricating oil clean, slurry pump run-time bearing temperature generally not exceeding 60 - 65 ℃ is appropriate, the maximum does not exceed 75 ℃.
5) To ensure the motond Other pumps pump coaxial and ensure the integrity of the coupling of elastic cushion is correct, damaged should be replaced on time.
6) To ensure that slurry pump components and piping system is installed correctly, solid and reliable.