ASTM F2599 - 11 Standard Practice for The Sectional Repair of Damaged Pipe By Means of An Inverted Cured-In-Place Liner
This practice is for use by designers and specifiers, regulatory agencies, owners, and inspection organizations who are involved in the rehabilitation of pipes through the use of a resin-impregnated tube installed within a damaged existing pipe. As for any practice, modifications may be required for specific job conditions.
1.1 This practice covers requirements and test methods for the sectional cured-in-place lining (SCIPL) repair of a pipe line (4 in, through 60 in. ) by the installation of a continuous resin-impregnated-textile tube into an existing pipe by means of air or water inversion and inflation. The tube is pressed against the host pipe by air or water pressure and held in place until the thermo set resins have cured. When cured, the sectional liner shall extend over a predetermined length of the host pipe as a continuous, one piece, tight fitting, corrosion resistant and verifiable non-leaking cured-in-place pipe.
1.2 The values stated in inch-pound units are to be regarded as the standard. The values given in parentheses are mathematical conversions to SI units that provided for information only and are not considered standard.
1.3 There is no similar or equivalent ISO Standard.
This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. Particular attention is drawn to those safety regulations and requirements involving entering into and working in confined spaces.
2. Referenced Documents (purchase separately)
D790 Test Methods for Flexural Properties of Unreinforced and Reinforced Plastics and Electrical Insulating Materials
D1600 Terminology for Abbreviated Terms Relating to Plastics
D3681 Test Method for Chemical Resistance of Fiberglass (Glass-Fiber-Reinforced Thermosetting-Resin) Pipe in a Deflected Condition
D5813 Specification for Cured-In-Place Thermosetting Resin Sewer Piping Systems
F412 Terminology Relating to Plastic Piping Systems
F1216 Practice for Rehabilitation of Existing Pipelines and Conduits by the Inversion and Curing of a Resin-Impregnated Tube
RecommendedSpecifica for Sewer Collection System Rehabilitation.
Sectional cured-in-place lining; tube; sheet; vacuum impregnate; continuous; bladder; textile; felt; knit; resin; inversion; inflation; ambient cure; steam cure; launcher; liner/bladder assembly;
ICS Number Code 23.040.99 (Other pipeline components)
ASTM International is a member of CrossRef.