Airmaster Aerator - Model Turbo - Aerators for Industrial Wastewater Treatment
Airmaster Aerator specializes in aerators, aeration, industrial wastewater treatment, pond aeration, wastewater aeration systems and aeration equipment. The Airmaster Aerator 'TURBO' aeration system is one of the most advanced and efficient aerator technologies available on the market today. Our industrial and municipal aeration equipment features stainless steel construction and a 'TURBO' blower to achieve maximum aeration.
With our toothed, synchronous drive system, we can change the speed, performance, and energy consumption of an aerator of a specific given horsepower. Each aerator produces two distinct mixing zones for complete mixing of the biomass.
These advanced wastewater aeration systems will help you meet regulations and permit limits. The aerator sizes available are 10 h.p. single phase and 10 h.p., 15 h.p., 20 h.p., 25 h.p., and 50 h.p. three phase aerators.
- Aerators that excel in extreme waste water conditions
- Wastewater aeration systems that help meet permit limits
- Replaces old aerator technology with up to three times the reduction in horsepower
- Advanced industrial wastewater treatment technology
- High capacity water movement with aeration incorporated in a discharge manifold
- A turbo air blower in conjunction with an oxygen generator to achieve the maximum oxygen transfer available
- Oxygen transfer over 3.0 pounds of oxygen per nameplate horsepower per hour (under normal conditions)
- Stainless steel construction
- Effective in sludge reduction
- Effective in B.O.D. AND C.O.D. reduction
- Effective in algae control
- Synchronous belt Drive System
- No gear boxes, reducing the risk of mechanical failure
- Maintenance free bearing system
- Hinged intake housing for ease of cleaning
- Effective in odor reduction
- De-foaming spray
- Floatation has an expanded polystyrene core with hybrid urethane coating impervious to diluted acids, alkalines, and petroleum products
- Unique design enhances the performance of existing aeration equipment
- Able to change the speed, performance, and energy consumption of aerator
- Performance exceeds aerators over twice the horsepower
- Available in 10 H.P. to 50 H.P.
- One year warranty
- The following specifications cover the performance, design, construction, and installation of the floating aeration equipment.
- Each aerator shall be capable of producing 3.0 lbs. of oxygen per nameplate horsepower per hour under normal conditions. Each ____ HP aerator shall be capable of pumping and mixing approximately 1,908,000 to 12,500,000 gallons per day (depending on horsepower) under normal conditions and continuous operation.
- The aerator shall produce two or four (depending on horsepower) distinct mixing zones within the lagoon cell for complete mixing of the biomass.
- The aerator shall have one-third of the liquid being pumped, directed into a high-pressure spray. This spray shall be used for aeration, stripping gases from the liquid, and as a de-foaming spray.
- The aerator shall have a synchronous belt drive system and shaft driven to allow the owner to vary the speed and performance of the aerator in the field. A gear box or gear reducer shall not be used.
- Motor - The motor shall have the following features:
- Motor shall comply with EPACT ’92 efficiency standards.
- Service factor of 1.15 to 1.25 (depending on motor type), over the motor nameplate at 60 HZ.
- Class F insulation.
- Double shielded bearings with re-greasing provisions on the shaft end.
- Motor shall be designed for 230 1-phase or 208, 230 or 460 volt, 3-phase operation.
- Motor shall be IEEE Series 841, Hostile Duty, or aluminum motor.
- Frame and Components shall be fabricated of 304-L stainless steel. A 304-L electrical conduit tray shall be provided for securing the electrical conduit. Stainless steel lifting lugs shall be provided for equipment lifting.
- OPTIONAL (for an additional charge) A NEMA 4 stainless steel electrical junction box shall be provided with power block, grounding lugs, and pre-wired to the motor. The junction box shall allow the electrical contractor to terminate their power cable from the motor starter.
- Floatation – to have the following features:
- Floats shall be an expanded polystyrene core with a hybrid urethane coating.
- Coating shall be impervious to diluted acids, alkalis and petroleum products.
- Floats shall be covered with 304-L stainless steel expanded metal and designed to support the weight of two 240 lb. service technicians.
- Top bearings to be maintenance free “Double Roller” pillow block, concentric lock bearings lubricated with a solid oil lubricant having a load range of 20,200 ft/lbs.
- Bottom bearings to be maintenance free, Poly-Round Solution® or ALL-ROUND Solution® , pillow block bearings.
- Drive system to be “Poly-Chain GT2® ”. The toothed, synchronous belt is constructed of non-stretch material to prevent retensioning.
- Inlet intake cage shall be of 304-L stainless steel construction and hinged for ease of cleaning. A 1/4” stainless steel lifting chain shall be provided.
- Motor Hood shall be of 304-l stainless steel construction. The motor hood shall cover the motor, drive belt, and the “Double Roller” pillow block bearings. The motor hood shall be hinged for ease of access to the above-mentioned parts with a safety-locking device installed to eliminate accidental closure of the motor hood. The motor hood shall be constructed to prevent direct exposure to rain, sleet, snow, sun, and water spray.
- OPTIONAL (for an additional charge) A 304-L stainless steel standoff assembly shall be provided for anchoring of the aerator. The stand-off assembly shall be secured to the lagoon bank through two 304-L stainless steel spud legs. The other end of the stand-off assembly shall be connected to the aerator through 304-L stainless steel receptacles fixed to the end of the frame assembly. The stand-off assembly allows the aerator to be positioned the desired distance from the lagoon bank and shall be designed to allow the operator to move the aerator to the bank for routine maintenance and inspection. No mooring cables or anchors shall be required to secure the aerators in position.
- The aerator shall be warranted for defects in materials and workmanship for the period of one year from date of start-up, or 18 months from date of shipment, whichever occurs first.